Q: The Joint Commission standard for weekly testing of the fire pump only requires us to record the test date of the inspection. We were cited for not recording the suction and discharge pressures. Is this a requirement?
A: Yes, recording the suction and discharge pressures, along with the amount of time required to start the weekly test (by lowering the water pressure) are required documentation for each weekly fire pump test. Even though these requirements are not specifically identified in the EC standards, they are identified in the NFPA 25 (1998 edition) which is referenced by the Joint Commission standards.
Get a copy and read the NFPA 25 (1998 edition) as it has a lot of testing requirements of the sprinkler system which are not identified in the Joint Commission standards, but are required.