Q: There is an existing clinic which is classified as business occupancy that leases space within a rehabilitation and nursing center. Does this need to be separated by a 2 hour rated partition? Does the egress corridor from the clinic to the exterior need to be rated?
A: Uhm… my answer is … it depends. You state the clinic is a business occupancy, but you did not state what occupancy the rehabilitation and nursing center is. I’m not sure what you mean by a ‘nursing center’… is that a hospital, a nursing home, or is it something else? Is the rehabilitation center classified as a hospital or a nursing home? Or is it outpatient only? Are there any patients in the rehabilitation center that are incapable of self-preservation? If so; how many?
If the rehabilitation center and the nursing center is a different occupancy than the clinic (which you say is a business occupancy), then yes, the different occupancies must be separated by fire rated barriers. The fire rating of these barriers depends on whether or not the occupancy (other than the business occupancy) is healthcare occupancy. Where healthcare occupancy is separated from any other occupancies, the fire rating on the barrier must be 2-hours. However, if the occupancy of the rehabilitation and nursing center is not healthcare occupancy, then the fire rating on the barrier separating the occupancies is only required to be 1-hour rated.
Corridors in new construction business occupancies must be constructed with 1-hour fire rated walls, according to section 188.8.131.52 of the 2012 LSC. But the exceptions to 184.108.40.206 say the requirement for 1-hour fire rated walls does not apply:
- Where exits are available from an open space;
- Within a space occupied by a single tenant;
- Within buildings protected throughout by an approved sprinkler system.
If the business occupancy is considered existing construction, then there are no requirements for the corridor walls. If the rehabilitation and nursing center exits into and through the business occupancy, then the corridor in the business occupancy must meet the requirements for corridors in the occupancy where the rehabilitation and nursing center is located.