Q: Is there a code requirement for testing magnetic-locking devices, for a facility maintenance director?
A: There is a requirement in NFPA 72-2010, section 14.4.5 that all interface devices (i.e. relays, control modules) be tested once per year. Since the magnetic locks in access-control and delayed egress locks are connected to the fire alarm system via an interface relay, then the magnetic lock needs to be tested once per year to ensure it disconnects during a fire alarm signal. This test is required to be conducted by someone who is certified in accordance with NFPA 72.
If you are CMS certified or accredited by any of the major accreditation organizations then you would be expected to comply with the manufacturer’s recommendations on preventive maintenance. Most manufacturers of magnetic locks requires periodic maintenance to ensure they are functioning correctly.