Q: During a recent survey we were almost cited because one of the fire extinguisher signs was on the front of the fire extinguisher cabinet and the rest were above the cabinets. The surveyor warned us that all of the signs needed to be the same. Is that true?
A: Well, I’m glad the surveyor did not cite you for this. If he/she had, you could have easily appealed this away after the survey. The 2000 edition of the LSC requires compliance with NFPA 10 Standard for Portable Fire Extinguishers (1998 edition). Section 1-6.12 of NFPA 10 says fire extinguishers mounted in cabinets or wall recesses must be placed so that the fire extinguisher operating instructions face outward. The location of such fire extinguishers must be marked conspicuously. Section 1-6.6 says extinguishers should not be obstructed, but if they are then ‘means shall be provided to indicate the location’ and the Annex portion of 1-6.6 describes acceptable means, such as arrows, lights, signs, or coding of the wall or column. Nowhere does it say all of the fire extinguishers have to be marked the same way or method. Now, I’ll admit that it is obvious to me that they all should be marked the same way for continuity purposes, but I do not see where the standard requires that. Therefore, based on your comment that the surveyor ‘almost’ cited you but did not, indicates to me that he/she felt the same way that I do that the extinguishers should be marked the same way, but it is not a standard requirement, therefore no citation was made. So, no the extinguisher cabinets don’t have to be marked the same way, but it sure makes sense to do so. I suggest you have someone correct this so they all are marked the same way.