I received a telephone call recently from a lawyer that asked me if I would be willing to serve as an expert witness in a pending litigation suit. The situation of the lawsuit is a patient who was admitted to the inpatient psychiatric unit of a hospital busted the protective cover over the fire alarm manual pull station, and activated the fire alarm system. The entrance doors to the psychiatric unit unlocked on the fire alarm, and the patient ran out, climbed to the roof of the facility and jumped off.
Now the family of the patient is suing the hospital and the fire alarm company who installed the interface between the door locks and the fire alarm system. The plaintiff’s lawyer is arguing that the interface should never have been installed and the doors should not have unlocked upon activation of the fire alarm system. I agree with the plaintiff’s lawyer, but the problem is, it was the defense’s lawyer who contacted me.
The two major codes and standards that apply in this situation are the NFPA 72 National Fire Alarm Code (1999 edition), and the NFPA 101 Life Safety Code (2000 edition). The Life Safety Code (LSC) allows clinical needs locks on doors in the path of egress, but only in healthcare occupancies (hospitals). They are not permitted in any other occupancy. These types of locks are permitted where the “clinical needs of the patients require specialized security measures for their safety, provided that staff can readily unlock such doors at all times”. Clinical needs locks are permitted for Behavioral Health units, such as psychiatric and Alzheimer units, to prevent patients from leaving the unit unauthorized, and potentially harming themselves or others. Clinical needs locks requires all staff who work on that unit (which includes physicians, nurses, aids, clerical, maintenance, foodservice, housekeeping, etc.) to have a key or device to unlock the door on their person at all times. [Code reference: 188.8.131.52.4, Exception No. 1, 2000 edition of the LSC].
But when it comes to connecting those clinical needs locks to the fire alarm system so they automatically unlock on a fire alarm activation, the codes are not so clear. Other permissible locks, such as delayed egress locks and access control locks, are required by code to be connected to the fire alarm system and automatically unlock the door whenever there is an alarm. However, there is no such similar language for clinical needs locks to unlock on an alarm. In addition, NFPA 72 section 3-9.7.1 and 3-9.7.2 says if you have a lock on an exit door it must be connected to the fire alarm system, and it must unlock the door on a fire alarm. However, the exception to 3-9.7.2 essentially says this is not required if an AHJ says so, or if another code says so. So, we go back to the Life Safety Code, and we see that delayed egress locks and access control locks are required to unlock on an alarm, but the section on clinical needs locks is very silent on the subject. When a code is silent on a subject that means it is open for interpretation. Therefore, section 3-9.7 of NFPA 72 does not apply to clinical needs locks in a hospital, because the interpretation Life Safety Code permits it. It is documented that psychiatric patients are astute enough to actuate a fire alarm to unlock the exit doors. Therefore, the code is available to be interpreted in such a way to not require clinical needs locks to unlock the doors in the path of egress on activation of the fire alarm system provided all staff carry a key to unlock the door in case of an emergency.
But who makes that interpretation? Usually the authorities having jurisdiction (AHJ) makes that interpretation. Section 184.108.40.206 of the 2000 LSC says the AHJ shall determine whether the provisions of the LSC are met. But when the AHJ does not issue an interpretation, then it is up to the individual organization’s to decide. As far as I know, there is no national AHJ for healthcare that has it written in their standards that clinical needs locks should not be connected to the fire alarm system. Therefore, the hospital needs to ask the question: Based on the potential risk to patient safety, is it best to connect the door locks on the psychiatric unit to the fire alarm system so they unlock upon activation of the fire alarm system?
I declined the offer to be an expert witness for the defense, and suggested they settle the lawsuit out of court.