Q: A deficiency was found by CMS on a recent survey that stated ‘staff failed to provide a safe and hazard free environment by not having all doors protecting corridor openings ready to close without impediments’. The finding was repeated three separate times as doors to a patient room could not be closed due to obstructions/impediments. In all three instances, the rooms were vacant, being used for storage, and had either a chair or waste basket blocking the door. Although we have regularly explained away this finding with Joint Commission surveyors as being an item we train our staff on (to move obstructions in patient room doorways in case of fire while closing all doors as directed by our fire plan) the CMS surveyor listed it as a deficiency and was not satisfied with our answer. Does this seem like a reasonable action to you? The rooms were vacant, and there were no patients in the rooms! Why would the CMS surveyor care if the doors closed or not? Do I have to attempt a zero-tolerance approach to this deficiency for all patient room doors (which would seem to be futile) or just enforce the regulation for vacant rooms only?
A: Corridor doors must close and latch at all times in the event of an emergency. Even corridor doors to vacant patient rooms used for storage.
I believe by what you have described, that the CMS surveyor was correct and justified in citing any corridor door that could not close. If there was an impediment blocking the door, such as a chair or a waste receptacle preventing the door from closing, then that is a deficiency. Here is the reason why… In an emergency, staff must quickly go through the unit and check rooms and close doors. If there is an impediment to quickly closing the doors, and the staff had to move a chair or a waste receptacle, then that slows down the process. The concept of the corridor door is to separate the room from smoke and fire in the corridor. If an impediment prevents the door from closing, then smoke and fire can enter the patient room and then the patient is in serious trouble.
You must enforce maintaining the corridor doors free from impediments to close them throughout your entire hospital, on units that are occupied and units that are not. I do not agree with your comment that seeking a zero-tolerance on this issue would seem futile. On the contrary, nurses have a very keen respect for patient safety, and if you explain keeping corridor doors free of impediments is patient safety, then I’m sure they will buy into that and keep the doors clear.
I’m a bit concerned that you are using vacant patient rooms for storage. Be VERY careful with that. If there are any combustible stored in those patient rooms, you have a big problem. The room would have to comply with section 188.8.131.52 (2) of the 2012 LSC on hazardous rooms. I would suggest you do not store any combustibles in vacant patient rooms.