Q: We have a behavioral health unit and want to know if pull-cords are required on the nurse-call system in the patient bathroom? Is there an alternative to cords so this type patient can’t hang themselves?
A: The NFPA codes and standards do not address this issue, but the FGI Guidelines do. CMS and the accreditation organizations expect you to follow the FGI Guidelines for new construction, unless there are other more restrictive requirements for other authorities, such as state health departments or local building codes.
Section 2.5-22.214.171.124 of the 2010 FGI Guideline says a nurse call system is not required in psychiatric nursing units, so you do not have to provide cords on the call-buttons. Also, section 2.5-126.96.36.199 says call cords or strings in excess of 6 inches are not permitted. Now, the latter section is for geriatric, Alzheimer’s, or dementia units, but the concept can carry-over to your behavioral health unit.