Q: We have a potential elopement risk at the nursing home where I work. A patient gets into the stairwell and down to the first floor and exits the building. We have an alarm system that alerts us when any door is activated. My question is: Can we install interrupter gates on the second floor leading down to the first to deter elopement risk?
A: I’m not sure what you believe to be an interrupter gate … but they won’t do you any good in restricting egress. By definition, an interrupter gate cannot restrict egress. If you are fully sprinklered, you can install delayed egress locks that will slow down egress for 15 seconds, allowing staff to respond to the local alarm and prevent someone from leaving. For normal egress you can provide authorized people ID badges that can be swiped or read on a card reader bypassing the delayed egress locks. You may even consider specialized protective measure locks as described in section 184.108.40.206.5.2 of the 2012 LSC. They may cost you more, but they are effective for your concern.