Q: I have always tested my fire pumps on a weekly basis, but now I’ve heard from a consultant there is a new standard that says only a monthly run is required. Is this true?
A: Yes, it is. With the adoption of the 2012 Life Safety Code, the 2011 edition of NFPA 25 is now the standard to use regarding inspection, testing and maintenance of sprinkler systems. Section 184.108.40.206 of NFPA 25-2011 now allows electric-motor driven fire pumps to be tested under no-flow conditions on a monthly basis rather than weekly, which was required under previous editions of NFPA 25. However, engine-driven fire pumps still must be tested weekly.