Q: During a recent survey, the surveyor said a card reader on the stairwell door cannot be located on an adjacent wall or door frame, but it must be an integral part of the lockset itself. Is this true? They were talking about card readers on the stairwell side for re-entry to a floor.
A: Did the surveyor cite you for non-compliance? If not, surveyors sometimes say things that are misunderstood, especially if there is no citation. Doors not in the path of egress are permitted to be locked, and a re-entry door from a stairwell usually is not in the path of egress. As long as the re-entry door in the stairwell is not in the path of egress then I do not see any reason that what you describe would be a problem. The Life Safety Code would allow for a card reader device to unlock a stairwell re-entry door as long as the door is not in the path of egress. If the card reader is mounted in the stairwell on the door leading to a floor of the building (not a discharge door), then the card reader is not on the egress side of the door. There is nothing in the Life Safety Code, or in NFPA 80 Standard for Fire Doors and Fire Windows, (1999 edition) that would require the card reader to be mounted on the door leaf, rather than the on the wall near the door. Therefore, it is clear that the LSC permits card-access readers to be mounted on the wall near the door, since it is not a device or motion to operate the door. I cannot think of any situation that would require the card-access reader to be mounted on the door leaf, itself.