Q: What section of NFPA 72 (the National Fire Alarm Code) requires ambulatory surgery centers to perform testing of their fire alarm system on a quarterly basis? Do devices that require annual testing have to be divided and have the service contractor do 25% of them each quarter? My organization would like to know the specific identifier so that the requirement may be referred to.
A: The quick answer is there is no requirement in NFPA 72 (or any other NFPA standard) that requires quarterly testing of the fire alarm system for ASC classified as ambulatory care occupancies. Section 22.214.171.124 of the 2000 edition of the LSC requires compliance with section 9.6. Section 126.96.36.199 requires compliance with NFPA 72 (1999 edition) for testing and maintenance. NFPA 72, Table 7-3.2 discusses the frequency of testing and inspection for each component and device of the fire alarm system. While there are a few items that require quarterly testing (such as water-flow switches on sprinklers system, which actually comes from NFPA 25, and off-premises emergency notification transmission equipment), for the most part, annual testing is required on all initiating devices, notification devices, and interface devices. You do not have to divide the components that require annual testing into four groups and have your service contractor perform testing on 25% of the devices on a quarterly basis. Actually, this can be troublesome for larger organizations if the service contractor fails to test the devices during the same quarter each year. Most accreditation organizations require the annual test to be performed 12 months from the previous test, plus or minus 30 days.