Q: We have an Ambulatory Surgical Center (ASC) located in a one story nonsprinklered building, and is separated from a physician’s office. The exit access from the ASC leads into a corridor which is within the physician’s practice. Since this corridor is not technically part of the ASC, is the ASC responsible for having the corridor wall opposite from the occupancy separation to be 1-hour fire rated?
A: You raise an excellent point: Once you leave the ambulatory health care occupancy and enter a different occupancy type, does the means of egress have to comply with ambulatory health care requirements? According to sections 20/126.96.36.199 of the 2000 edition of the Life Safety Code (LSC), the answer is yes. This section says all means of egress from ambulatory health care occupancies that traverse non-ambulatory health care spaces must conform to requirements of the LSC for ambulatory health care occupancies. The exception to this requirement would be if the barrier between the ambulatory health care occupancy and the contiguous occupancy qualifies as a horizontal exit, then the means of egress in the contiguous occupancy does not have to meet the more rigorous requirements for ambulatory health care occupancy, provided the means of egress is not through a high-hazard area. Horizontal exits are required to be 2-hour fire rated. So, how does this apply to you? If your ASC qualifies as new construction (built after March 11, 2003), then the means of egress in the physician area (outside of the ASC) must have 1-hour fire rated walls that extend from the floor to the deck above (unless they terminate at a ceiling that is also 1-hour fire rated); or if the building is protected with automatic sprinklers throughout; or the barrier between the ASC and the physician’s offices is a 2-hour fire rated horizontal exit. If the ASC qualifies as existing construction (built on or before March 11, 2003) then there are no requirements for the corridors, and what you currently have would be acceptable.