Q: Can you give me some direction in the Life Safety Code on where alcohol-based hand rub (ABHR) dispensers are not allowed in business occupancy corridors?
A: Take a look at section 22.214.171.124 of the 2012 LSC. It says hazardous areas shall be protected in accordance with section 8.7. Section 126.96.36.199 says “No storage or handling of flammable liquids or gases shall be permitted in any location where such storage would jeopardize egress from the structure unless otherwise permitted by 188.8.131.52.” Section 184.108.40.206 discusses the various methods to store flammable liquids. ABHR product is mostly alcohol which is a flammable liquid; therefore, it is not permitted in any location that would jeopardize egress (i.e. corridors).
Section 220.127.116.11 does not apply to healthcare occupancies because section 18.104.22.168 actually permits ABHR dispensers in egress corridors. Similarly, section 22.214.171.124 does as well for ambulatory health care occupancies. But, chapters 38 and 39 do not have any such language… therefore, ABHR dispensers are not permitted in egress corridors of business occupancies.
If you’re wondering, when the requirements in the core chapters (chapter 1 – 10) differ with the requirements of the occupancy chapters, the occupancy chapters govern (see section 126.96.36.199).