Q: With the adoption of the new 2012 Life Safety Code by CMS, we had a discussion about projections from the corridor wall. Since the LSC only allows projections to be 4 inches, the question that came up was in regards to fire extinguishers mounted to the wall and not recessed as they project out from the wall about 7 inches. Will we be required to recess them or will they be allowed? The same question was raised about wall mounted telephones?
A: Actually, the 2012 LSC allows a 6-inch projection into the corridor [see 126.96.36.199(4)], but CMS’ Final Rule published May 4, 2016 said they will enforce the more restrictive 4-inch maximum projection into the corridor, based on the Americans with Disabilities Act (ADA). For all healthcare facilities that receive Medicare & Medicaid funds, they must comply with CMS’ exception to the 2012 LSC.
To answer your question, there are no exceptions to the 4-inch maximum projection rule. So, anything projecting more than 4 inches into the corridor, including fire extinguishers and telephones, would likely be cited by a surveyor or inspector.
I read a survey report just the other day where the surveyor cited the hospital for having an ABHR dispenser that projected into the corridor by 4 1/4 inches. So, AHJs are citing anything that projects more than 4-inches into the corridor, including fire extinguishers.
This may be a good opportunity to consider oval-shaped fire extinguishers that do not project more than 4 inches into the corridor. Take a look at these compliant fire extinguishers from Oval brand: http://ovalfireproducts.com/