Q: We have a double egress, cross-corridor door which will enter a suite under a renovation project. The suite wall is also an existing smoke barrier wall, separating smoke compartments. However, we do not want an exit route through the suite, as this would be a code violation. The new layout will not cause a dead-end corridor and the suite will house less than 50 people. Is it allowable to replace the double egress door with a pair of out swinging doors?
A: As long as the new doors are not cross-corridor doors, I believe you can have a pair of single-egress doors as an entrance to the suite in a smoke compartment barrier. Under section 184.108.40.206 of the 2012 LSC, all new cross-corridor doors serving a smoke compartment barrier must be the double egress type. But from your description, it appears these new doors would not be cross-corridor doors, but would be corridor entrance doors to the suite.
These new doors would have to latch because they are corridor entrance doors to a suite, even though they serve a smoke compartment barrier.